1, the production of cable joints, cable terminals and connectors, from the stripping of wire and cable should be continuous operation until the completion of shortening the insulation exposure time. Stripping the cable should not damage the core and retain the insulation. Additional insulation wrap, assembly, heat shrink, etc. should be cleaned.
2, oil-filled cable lines have joints, should first make joints; both ends of the difference, you should first make low-end terminal.
3, cable terminals and joints should be taken to strengthen the insulation, sealed moisture, mechanical protection and other measures. 6kV and above the power cable terminal and connector, should still have to improve the end of the cable shield electric field concentration of effective measures, and should ensure that the external insulation and the distance between the ground. 66kV and above cross-linked cable terminals and connectors made before the cable should be required to heat straightening. The installation process should be in accordance with the installation instructions and installation drawings.
4, three-core oil and paper insulated cable should be retained package insulation 25mm, shall not be damaged. Stripped shielded carbon ink, the end should be flat. Bending the core should be uniform force, should not damage the insulating paper; wire core bending radius should not be less than 10 times its diameter. When wrapped or filled with insulating material, the waterproof connector should remove the air gap at the core branch.
5, oil-filled cable terminals and connectors wrapped around additional insulation, shall not be completely closed pressure box. In the production and vacuum treatment, the oil leaking from the cable should be discharged in time, not in the porcelain sleeve or shell.
6, cable core connection, should remove the core and connecting pipe wall oil and oxide layer. Crimping mold and fittings should be appropriate. Compression ratio should meet the requirements. After crimping, the crowns on the terminals or connecting pipes should be repaired and the burrs should not be left. Use soldering copper core, should use the neutral solder paste, not burn insulation.
7, three-core power cable connector on both sides of the cable metal shield (or metal sets), armor layer should be connected well, not interrupted. The metal sheath of the buried cable connector and the metal sheath of the cable shall be protected against corrosion.
8, three core power cable terminal metal sheath must be well grounded; plastic cable for each phase of copper shield and steel armor should be welding ground wire. Cable through the zero sequence current transformer, the cable metal sheath and ground wire to be insulated, the cable grounding point in the transformer below, the ground wire should be directly grounded; grounding above the transformer, the ground wire should be through the transformer Ground. Single-core power cable metal sheath grounding should meet the design requirements.
9, single-core power cable cross-box, grounding box, protective cover and other cable accessories should be installed to meet the design requirements.